Fire hydrant flow testing provides important field information to water service planners and fire services so they can accurately estimate the capabilities of water mains. Testing uncovers any mechanical problems. Hydrants are tested, inspected and maintained to the requirements of section 57 of the water industries Act 1991.
- Hydrant frame
- Surface surrounding the hydrant
- Indicator plate
Wet pressure test
Fitting a stand pipe to the outlet, partially opening the valve to allow a small amount of water to flow. A blank cap is fitted in the stand pipe head and the hydrant fully opened. Whilst under pressure, all joints are to be visually inspected for signs of leakage and only those leakage’s that would impair the hydrant for fire-fighting purposes, or cause a hazard would be reported immediately.
Static pressure test
The static pressure test is conducted be attaching the static pressure assembly to the stand pipe with the vent cock open. The hydrant is then opened and the vent cock is closed when the stand pipe is free of air. A pressure reading is then taken. The hydrant is then closed and then the vent cock is opened to release the pressure before removing the stand pipe assembly.
Before attaching the flow tube to the hydrant stand pipe the main be flushed for a short period of time, approximately 1 minute, to clear any debris which may cause damage to the flow sensor. After flushing, the flow tube is attached to the stand pipe and the hydrant valve is fully opened. The digital display is left settle before any readings are taken.